POWER LINES SWITCHING
High-quality connection of equipment to any telecom operator.
As a telecom operator, FSUE TTC Ostankino pursues a neutral policy when the Client chooses the required telecom operator.
Before placing equipment in a data center, it is necessary to plan the telecommunications infrastructure, select communication systems for connecting the placed equipment.
It is possible to introduce the Customer's FOCL into the data center. For this, there are two wells in the city cable drain. Fibers, L1 (Lambda) links, DWDM, Internet access links may be required. It is necessary to conduct a study with the technical service of the data processing center of the technical feasibility of laying connecting lines between the racks, between the computer rooms of the data center and third communication service providers that have points of presence in the data center and in the TV center.
Provide for the installation of your own or rental of patch panels (patch panels) in racks.
THE SERVICE INCLUDES
CONNECTING TO ANY OPERATORPlacement of telecommunication equipment in separate cross rooms.
SLA 99,982 %Uninterrupted infrastructure. Fault-tolerant architecture withstands complex incidents.
REMOTE SERVICE24-hour duty of operational and technical personnel.
In accordance with the recommendations for the construction of fault-tolerant technological sites of the Tier 3 level, the TTC Ostankino data center is equipped with a redundant (N + 1) engineering infrastructure that ensures uninterrupted operation of equipment and the best conditions for the provision of equipment placement services - Сolocation. The data center is located in a fenced area of 10,000 sq.m. The electrical power supplied to the facility - 11 MVA - is sufficient to connect powerful computing clusters. Spacious server rooms and auxiliary rooms allow you to work in a comfortable environment. The new engineering equipment has a huge operational reserve. Design solutions allow carrying out maintenance of any engineering system without interruption in the provision of services to customers.
4 server rooms and 2 cross rooms for 700 racks are in operation
Industry security compliance
Dispatch of work in the data center and round-the-clock monitoring
24/7 "remote hands" support
Neutral policy when connecting to telecom operators
Four independent urban substations and a direct connection to CHPP-21, together with an automatic transfer switch system, make it possible to classify the power supply of the data center as a special group of the first reliability category. The elements of the data center power supply circuit are reserved according to the N + N scheme. Server rooms are equipped with two busbar systems connected to independent UPS groups with a capacity of 1 MW. The average power consumption of the rack is 6 kW. It is possible to organize zones with increased rack power consumption. Crossrooms are equipped with independent UPSs.
Automatic switching between inputs
Two three-phase IEC309 inputs to each rack with 16 / 32A circuit breakers
Two PDUs with C13 / C19 sockets
Earthing of racks in accordance with PUE and GOST R 50571-4-44-2011 “Safety requirements. Protection against voltage deviations and electromagnetic interference "
Monitoring system of quality parameters of power supply in server and cross rooms
The refrigeration and air conditioning system of the TTC Ostankino data center is based on four chillers from well-known companies with the free-cooling function, with a total refrigerating capacity of 4.5 MWt. It uses a traditional system of supplying chilled air to the racks through the raised floor space. Redundancy of components of the refrigeration system is organized according to the N + 1 scheme. The temperature and humidity conditions in each server room are maintained by six precision air conditioners and controlled in the hot and cold aisles by temperature and humidity sensors.
Raised floor height 1.2 meters
Cold and hot corridors organized
Two independent pump and pipe circuits
Room temperature 18-27 ° С, humidity 30-70%
Supply ventilation and overpressure maintenance in server and cross rooms
Compliance with ASHRAE-2011 TC 9.9 recommendations
To prevent fires, all technological premises of the Data Center are equipped with the Vesda Laser Line super-early smoke detection system. The gas fire extinguishing system uses 3M ™ Novec ™ 1230 extinguishing agent, which has the best environmental performance, providing a high level of safety for people and property. In accordance with fire safety requirements, the system is equipped with a double gas supply. Elimination of fire is carried out without disconnecting the power supply to the equipment. Staff rooms are equipped with fire detectors.
100% fire compliance
Direct control by employees of the Fire Department-93
Smoke and gas removal systems
Particular attention in the data center is paid to information and physical security. There are two security lines at the strategic data center facility: The first line - the outer perimeter and the entrance zone are guarded by a special police battalion and are equipped with intrusion detection systems. The second line is the internal posts of the private security company, located in front of the entrance to the adjacent territory and to the data center building. The security video surveillance system provides round-the-clock monitoring and video registration in all zones and premises of the data center and in the surrounding area. All data center premises are equipped with an access control system (ACS). When clients contact us, a multi-factor authorization system is used.
Multi-layered physical protection of the data center
Ready for PCI DSS certification
Storing video recordings for at least 30 days
Customized rack keys on demand
All server rooms of the TTC Ostankino data center are identical and are designed to accommodate up to 170 racks with a total capacity of 1 MW. At the moment, four halls have been commissioned. Server rooms are pressurized sealed rooms that protect equipment from dust penetration. Server rooms contain 45U high cabinets, 600x1200 and 600x1070 in size. All server cabinets are equipped with two PDUs with C13 and C19 sockets. To maintain the set temperature parameters, "cold" and "hot" corridors are organized, separating the air flows. Rack spaces have been prepared for placing standard and non-standard customer racks.
Average power supply 6 kW per rack
Power supply of racks by two independent inputs
Separated tray systems for fiber-optic communication lines and SCS
DPC "TTTS Ostankino" pursues a neutral policy in interaction with telecom operators, providing connection of the client's equipment to any telecom operator. The equipment of telecom operators is located in dedicated cross rooms of the data center (meet-me-room). All types of connecting lines are laid using two independent cable tray systems. Two cross halls with 10 racks were put into operation. Two independent inputs from the city telephone sewer
Free FOCL input
45U 800x1200 Racks
Copper and Optical Cross Connections
Connecting lines to any point in the Ostankino TV Center
The automated dispatching and control system allows real-time monitoring and control of all components of the data center engineering infrastructure. The 24-hour Dispatch Service controls the temperature and humidity conditions in the server rooms and cross rooms and maintains the proper functioning of all engineering systems of the data center. The duty shift conducts regular rounds of the data center and reacts to any deviations in the functioning of engineering systems and IT equipment. The services provided to customers are accounted for by an automatic system for collecting and processing data on consumed resources.
Over 1500 control points
Dispatch service 24x7
Annual maintenance schedule
Separate territory in the center of Moscow, parking for clients.
Three city inputs, up to 15 MW. 6kW per rack, metering the power of each rack.
Connected dedicated racks, placement of any customer racks.
New infrastructure, dispatching, engineering support 24/7.
Video surveillance of racks without dead zones. 24/7 security at the strategic facility level.
REPAIRS WITHOUT SHUTDOWN
Backup systems allow for scheduled repairs and maintenance without affecting customers.
Data center description
Free rack spaces for customer site development
Commissioned 700 rack-places
11 MVA - connection power
Design Average Power: 6kW per rack
DC «TTC OSTANKINO»
Location address DC
Mosсow, 1 Ostankinskaya str., 1/1
127427, Akademika Koroleva, 12
+7 (495) 617-77-00
+7 (495) 617-52-42